When assessing pump piping applications, it may be helpful to look at several alternative solutions for the same application and compare the different axial and lateral end load conditions. Alternative solutions can include the incorporation of anchors, rigid pipe loops, traditional restrained or unrestrained rubber expansion joints, and more advanced rubber expansion joint arrangements.

In Illustration 1, five alternatives are presented for a 36” diameter pump application with 25’ axial run of carbon steel pipe under 90 psi with temperature fluctuations of 50°F. Considered are 1/8” axial and lateral installation misalignment as well as 1/8” anticipated ground settlement. In this simplified assessment each solution will restrain the imposing loads and displacements, each with very different end loads.

Solution 1

This solution incorporates a main anchor near the pump. This anchored pipe solution is problematic because it directs potentially damaging loads and displacements from that section of piping back toward the pump. The carbon steel pipe will carry the full pressure thrust force in tension, but the pipe stress from thermal and misalignment displacements are tremendous. The axial end load can be determined using the axial force calculation for thermal stress, while assuming the lateral end loads can be calculated by other allowable pipe stress methods due to its relatively long leg length. The end loads for Solution 1 extend to a staggering 395,564 lbf axially and 32,812 lbf laterally.Solution 2

This solution incorporates an unrestrained expansion joint (Illustration 2) installed between a main anchor and the pump. This anchored pipe solution is also problematic because it directs potentially damaging pressure thrust force from that section of piping back toward the pump. The expansion joint absorbs the pipe stress from thermal and misalignment displacement well, however the pressure thrust force is quite large. The axial end load can be calculated as the sum of the pressure thrust force and the axial spring rate load of the rubber expansion joint. The lateral end loads can be calculated as the lateral spring rate load of the rubber expansion joint. The end loads for Solution 2 extend to an imposing 89,831 lbf axially and 670 lbf laterally.Solution 3

This solution incorporates a rigid pipe loop installed against the pump. This unanchored pipe solution works well when there are no space restrictions and the pipe loop can freely move away from the pump. The carbon steel pipe will carry the full pressure thrust force in tension; while the pipe stress from thermal and misalignment are within allowable pipe stress, they are still significant. The axial and lateral end load can be calculated using the M.W. Kellogg method for pipe loops. The end loads for Solution 3 extend to a less imposing 32,812 lbf axially and 32,812 lbf laterally.Solution 4

This solution incorporates a restrained rubber expansion joint installed between a rigid pipe loop and the pump. This unanchored pipe solution often works better because the restrained expansion joint absorbs the misalignment and ground settlement displacements while the pipe loop absorbs the axial thermal displacement. All components are restrained and will carry the full pressure thrust force in tension and do not transfer that load on to the system’s ends. The misalignment and ground settlement load can be calculated as the spring rate load of the rubber expansion joint. The axial terminal end load can be calculated using the M.W. Kellogg method for pipe loops. The end loads for Solution 4 extend to a more manageable 16,812 lbf axially and 670 lbf laterally.Solution 5

This solution incorporates an in-line pressure balanced rubber expansion joint installed between an intermediate anchor and the pump. This is the only effective solution for directly absorbing axial thermal movements with continual self-restraint of the pressure thrust forces. This advanced rubber expansion joint arrangement consists of tie devices interconnecting its main joint section to its opposing balancing joint section (Illustration 3). This is an optimal solution when there are load limitations on the pump and there is a high value placed on reducing the system footprint, as well as saving material and energy costs. The axial and lateral end loads can be calculated as the sum of the spring rate load of the in-line pressure balanced rubber expansion joint. The end loads for Solution 5 extend to a very manageable 1,406 lbf axially and 336 lbf laterally.When end loads on pump piping are a concern, optimal solutions are neither to increase rigidity into the piping system nor ignore the imposing pressure thrust forces as an effect of some expansion joint arrangements, but rather to incorporate axially restrained (tied) or more advanced rubber expansion joint arrangements.

---

*Author Lloyd B. Aanonsen, P.E., is President of General Rubber Corporation and has over thirty years of experience in the design, development and application of rubber expansion joints. He has a B.S. in Mechanical Engineering, an MBA, and is the author of numerous articles on the design and application of performance expansion joints. An active member of the Fluid Sealing Association (FSA) and the Hydraulic Institute (HI), he is also actively involved with the Electric Power Research Institute (EPRI) where he serves on a technical advisory group for rubber expansion joints.*